The European standard for controlled door closing devices is BS EN 1154 and only closers with this accreditation should be fitted to fire-resisting door as referenced in approved document B of the Building Regulations 1991.
Door closer are available in different power sizes, this is a means of varying the spring compression by increasing or decreasing the spring tension.
It’s very important to ensure the correct power size is specified otherwise the door may either not fully close the door or may be too stiff in its operation for people to use.
Power size table as referenced in BS EN 1154
Power size 1 – Maximum door leaf mass 20kg – maximum door leaf width 750mm
Power size 2 – Maximum door leaf mass 40kg – maximum door leaf width 850mm
Power size 3 – Maximum door leaf mass 60kg – maximum door leaf width 950mm
Power size 4 – Maximum door leaf mass 80kg – maximum door leaf width 1100mm
Power size 5 – Maximum door leaf mass 100kg – maximum door leaf width 1250mm
Power size 6 – Maximum door leaf mass 120kg – maximum door leaf width 1400mm
Power size 7 – Maximum door leaf mass 160kg – maximum door leaf width 1600mm
Example an average 30 minute fire door 2100mm (h) x 830mm (w) x 44mm thick would use a power size 2- 4 adjustable closer.
Door closer can be fitted in 3 different ways Figure 1 – The closer is mounted on the pull side of the door with the arm fixed to the frame. This is the most popular fixing and the most mechanically effective.
Figure 61- The closer is mounted on the push side the frame over the door.
Figure 6 – The closer is mounted on the push side of the door and the arm is fixed to the frame using a figure 66 bracket.
Please note if you are using the closer in the figure 6 configuration you will need to add a power size to ensure the door will close correctly.
Always very helpful and obliging. Always feel that things said will happen.
Mr D S Freezer Bognor Regis, West Sussex
Your people have been Helpful – Honest – Informative – Perfect, Thank you.
Alan Sharman Hindhead, Surrey
The transition of ownership of the company was seamless for customers with commitments and prices maintained.
Mr P Fxxxxxx Liss, Hampshire
The CIA technician was extremely courteous and knowledgeable, answering all my questions well.
Dr xxxxx Hampshire
Your staff are always pleasant, helpful and informative. It is also nice to have the same person every time to do the service.
Roger Garth Hutton Farnham, Surrey
Prompt, efficient service. Courteous and efficient technician.
Mrs G Richards Christchurch, Dorset
Polite and efficient engineer who treated us and our home with respect.
Mr L********* Rowlands Castle, Hampshire
CIA are easy to contact and their staff are helpful.
Martin Carter Clanfield, Hampshire
Always get good service and prices are competitive. Re-arranging appointments is easy and technicians always turn up as arranged.
Mr Evans Denmead, Hampshire
Technician was excellent, took care of my property, hoovered as he went along and took the time to channel the wiring properly and back filled as required – Absolutely first class service. I was hesitant to use CIA but friends recommended them and I am very pleased that I followed up on their advice.