The European standard for controlled door closing devices is BS EN 1154 and only closers with this accreditation should be fitted to fire-resisting door as referenced in approved document B of the Building Regulations 1991.
Door closer are available in different power sizes, this is a means of varying the spring compression by increasing or decreasing the spring tension.
It’s very important to ensure the correct power size is specified otherwise the door may either not fully close the door or may be too stiff in its operation for people to use.
Power size table as referenced in BS EN 1154
Power size 1 – Maximum door leaf mass 20kg – maximum door leaf width 750mm
Power size 2 – Maximum door leaf mass 40kg – maximum door leaf width 850mm
Power size 3 – Maximum door leaf mass 60kg – maximum door leaf width 950mm
Power size 4 – Maximum door leaf mass 80kg – maximum door leaf width 1100mm
Power size 5 – Maximum door leaf mass 100kg – maximum door leaf width 1250mm
Power size 6 – Maximum door leaf mass 120kg – maximum door leaf width 1400mm
Power size 7 – Maximum door leaf mass 160kg – maximum door leaf width 1600mm
Example an average 30 minute fire door 2100mm (h) x 830mm (w) x 44mm thick would use a power size 2- 4 adjustable closer.
Door closer can be fitted in 3 different ways Figure 1 – The closer is mounted on the pull side of the door with the arm fixed to the frame. This is the most popular fixing and the most mechanically effective.
Figure 61- The closer is mounted on the push side the frame over the door.
Figure 6 – The closer is mounted on the push side of the door and the arm is fixed to the frame using a figure 66 bracket.
Please note if you are using the closer in the figure 6 configuration you will need to add a power size to ensure the door will close correctly.
Prompt, efficient service. Courteous and efficient technician.
Mrs S******** Fareham, Hampshire
Always very helpful and obliging. Always feel that things said will happen.
Work carried out as requested and staff incredibly helpful as always.
Mrs Bell Camberley, Surrey
Had CIA at previous address and were so impressed with the level of service, we had one installed at our new address!
Mr A W***** Fareham, Hampshire
Whilst considering a security system installation, we noticed alot of properties in the area that had CIA alarm boxes installed and when we asked some local people about them, we discovered that CIA was a local well established company that had a good reputation. We’re pleased that we chose CIA as they have proven this […]
Mr Lockton – Rowlands Castle, Hampshire
Prompt service, helpful technicians, no attempt to sell us a ‘modernised’ alarm system.
Mr P Fxxxxxx Liss, Hampshire
The CIA technician was extremely courteous and knowledgeable, answering all my questions well.
Chris Holliday Guildford, Surrey
Your technician was exceptionally pleasant and helpful – a credit to your company
Roger Harvey Berkshire
Customer service has always been good and a great deal of time and effort was put into sorting out the issues we had with the system when it was first installed. We always found CIA to be a very reliable company and a company we would be more than happy to recommend.