The European standard for controlled door closing devices is BS EN 1154 and only closers with this accreditation should be fitted to fire-resisting door as referenced in approved document B of the Building Regulations 1991.
Door closer are available in different power sizes, this is a means of varying the spring compression by increasing or decreasing the spring tension.
It’s very important to ensure the correct power size is specified otherwise the door may either not fully close the door or may be too stiff in its operation for people to use.
Power size table as referenced in BS EN 1154
Power size 1 – Maximum door leaf mass 20kg – maximum door leaf width 750mm
Power size 2 – Maximum door leaf mass 40kg – maximum door leaf width 850mm
Power size 3 – Maximum door leaf mass 60kg – maximum door leaf width 950mm
Power size 4 – Maximum door leaf mass 80kg – maximum door leaf width 1100mm
Power size 5 – Maximum door leaf mass 100kg – maximum door leaf width 1250mm
Power size 6 – Maximum door leaf mass 120kg – maximum door leaf width 1400mm
Power size 7 – Maximum door leaf mass 160kg – maximum door leaf width 1600mm
Example an average 30 minute fire door 2100mm (h) x 830mm (w) x 44mm thick would use a power size 2- 4 adjustable closer.
Door closer can be fitted in 3 different ways Figure 1 – The closer is mounted on the pull side of the door with the arm fixed to the frame. This is the most popular fixing and the most mechanically effective.
Figure 61- The closer is mounted on the push side the frame over the door.
Figure 6 – The closer is mounted on the push side of the door and the arm is fixed to the frame using a figure 66 bracket.
Please note if you are using the closer in the figure 6 configuration you will need to add a power size to ensure the door will close correctly.
The engineers were excellent, hard-working, efficient and pleasant, and did a great job. They explained everything thoroughly. They were tidy and left the house as they found it.
Mr E A**** – Southampton, Hampshire
…a perfect example of first class customer service. Gareth & Chris went the extra mile to install the system as we wanted it – not as might have been easiest, and were always polite and considerate… As always, it’s the people that matter – very pleased.
Mrs N H***** Bournemouth, Dorset
Engineer arrived on time and was very friendly, willing to take on board our comments regarding box location from the moment he arrived – He went through the system and demonstrated it several times. He was thorough in his testing. He took extra care to hide the cabling, swept up and even offered to vacuum!
Alan & Gwen Waters Fareham, Hampshire
Always helpful with a swift service – would happily recommend to anyone interested in alarms.
Mrs J Gxxxx Southampton, Hampshire
Technician and office always pleasant.
Mrs J Baldwin Portsmouth, Hampshire
Service always top class, engineers polite and cheerful.
Mr D***** Hayling Island, Hampshire
Very Polite, cleared up any mess he made. Hardly knew he was in the house.
Martin Carter Clanfield, Hampshire
Always get good service and prices are competitive. Re-arranging appointments is easy and technicians always turn up as arranged.
Mr R Cecil Waterlooville, Hampshire
Appointment change was easy – Engineer was very helpful – Good Service
Mrs Hulmes Andover, Hampshire
Asked questions and checked we were happy – nothing too much trouble…and all with a positive approach and a smile!